Dongguan Sheng Guang Industrial Equipment Co.,Ltd.
Add: No.1 Luxi 2 Road Xixi Liao Bu Town, Dongguan.China.
If there is insufficient water flow in the chiller, it can generally be divided into two cases. First, the water flow is insufficient at the beginning of use, which is due to the mismatch of water cooler pump selection (because some lasers have strict requirements on water flow and head or the cooling water path is too long and too thin), and need to replace a larger power pump. Second, the original chiller can be used normally, but suddenly there is insufficient water flow, which may be due to pump failure or water blockage. At this time, Colida water chiller suggests that customers can take out the water pipe and use air pressure gun to open the water pipe, and then connect to observe whether the water chiller can operate normally, if the water chiller is running normally, it is because of water blockage; if the water chiller still has insufficient water flow, it is because the water pump of the water chiller is broken down, it will be a new one. A pump can be used.